Ate towel radiator: It is an ideal choice for those who are seeking a practical and stylish bathroom radiator. It is ideal for all modern settings both as a room divider and as a heated towel rail. It can be installed in any conventional heating system. Coloured radiator - we offer it in 208 colours without extra charge.
Benefits of this towel radiator: - versatile design radiator - coloured radiator, available in 208 colours - suitable for different heating types (central heating radiator, electric radiator and dual fuel radiator) - available in wall fixed and room divider versions - supplied with brackets or a room divider set (brackets and 150mm leg) - available accessories: manual valve set (coloured or chrome) and chrome thermostatic valve set MATERIAL(S) of this radiator: steel WARRANTY: 5 years DELIVERY SCHEDULE: approx. 6 weeks
Sizes of the Ate heated towel rail: Heights: 785mm high, 969mm high, 1215mm high, 1599mm high, 1783mm high – (electric & dual fuel versions: approx. +100mm) Widths: 500mm wide, 600mm wide, 750mm wide
Technical specifications: Heat outputs: All heat outputs are shown at operating temperatures of 75/65/20 (Δt50°C). All radiators have been manufactured and tested in accordance with DIN EN 442. Valves: These towel radiators are not supplied with valves. Connections: 4 x 1/2" BSP connections Centre-to-centre distance of connections: nominal width –48 mm Maximum operating pressure: 10 bar Maximum water temperature: 90°C Air Vent: All radiators are supplied with air vent valves. Brackets: All radiators are supplied with brackets. Finish: High quality, environmentally friendly, double electrostatic powder coating (burned Epoxy-Polyester coating for RAL colours) according to DIN 55900.
Dual fuel & electric only versions: All radiators have been manufactured and tested in accordance with DIN EN 60335. This fluid-filled towel radiator is equipped with an appropriate electrical heating element. Insulation: Class 1. Protection: IPX4. Thermostatic temperature controller: included (Please note that a thermostat is about 8-10cm long, therefore the distance between of the radiator and the floor should be minimum 15cm.) Warranty (on electrical parts): 2 years Output(s): depending on size
Warning! The minimum distance between of an electric/dual fuel radiator and a bathtub should be 60cm!
Please note the colours depicted on the chart below are for guidance only. The displayed colours are depending on your monitor settings and browser, so colours might not be shown perfectly. For this reason you may find differences between shade and hue on your screen and the radiator manufactured for you.
See the available colours HERE(in JPG format) andHERE in PDF format)
In order to avoid accidents keep to the following safety regulations:
INSTALLATION AND MAINTENANCE OF RADIATORS • All radiators must be installed and maintained by a certified professional, who provides legal guarantee for the work done. • The radiators must be installed exclusively by certified fittings provided by the manufacturer. • The radiator must be fixed soundly to the wall; as radiators are very heavy, torn out of the wall they can do extensive damage and seriously injure people nearby. • Radiators can be fixed to walls that can carry their weight. Too thin and drywall walls must be reinforced by a professional before installation. • Use the radiators strictly according to their purpose. • Radiator holders are designed to safely carry the weight of the radiator; for this reason never put any extra weight on it, cling to it or lean, sit or stand on it even for a second. • The radiator should not be placed behind or below furniture or other obstacle for the circulation of air. • The radiator can be damaged by mechanical force caused by hard objects, so avoid this by all means. • If you notice any damage, fracture, etc. on the radiator, switch it off immediately or turn off the heating. In the case of electric and dual fuel radiators disconnect the device from electricity.
HOT WATER RADIATORS • Faulty or damaged radiators can leak hot water, which might cause serious burn injuries. In case you cannot wait until it cools down touch the hot radiator with utmost care.
ELECTRIC AND DUAL FUEL RADIATORS • Electric and dual fuel radiators must be handled with the same level of caution and safety measures as any other electrical household appliances. • Keep the electrical cord intact. Cords must not get in contact with the hot radiator. • Electric/dual fuel radiators in rooms with running water can be installed only in areas determined by the IP Code provided with each electric/dual fuel radiator. The IP zones drawing can also be found with these models. (The IP Code, International Protection Marking, IEC standard 60529, sometimes interpreted as Ingress Protection Marking, classifies and rates the degree of protection provided against intrusion (body parts such as hands and fingers), dust, accidental contact, and water by mechanical casings and electrical enclosures.)
GLASS AND MIRROR RADIATORS • Although tempered glass, used for glass and mirror radiators, is many times stronger than float glass and complies with the EU standards, it is apparently not unbreakable, consequently it needs caution (despite the fact that, when broken, it usually will break into small fragments, which are less likely to cause serious injury.). • Do not let any mechanical force caused by hard and sharp objects damage the surface of the glass/mirror.
CHILD SAFETY • Unless the heating temperature is set low make sure that children are supervised near the radiator. As the body surface of a child is bigger than that of an adult, and their skin is considerably thinner, a hot radiator or hot water leaking from a damaged radiator can do more serious burn injuries to them. • Some radiator models have sharp edges, which can also cause injuries to children. For this reason, if you live with children, or have children around unsupervised, install only radiators with rounded edges. • Keep children away from the cord of the electric/dual fuel radiator. The best solution is wires hidden in the wall or the use of cord cover.